Minimum order is 10 feet.
Mfg description: STRANDED BARE COPPER CONDUCTORS, PVC-NYLON INSULATION, SUN-RESISTANT PVC JACKET, TESTED PER UL REQUIREMENTS FOR TYPE TC CABLES HAVING THWN OR THHN (TFFN) CONDUCTORS. CABLES ARE LISTED FOR DIRECT BURIAL. 90C, 600V
Tray Cable: This is the standard wire for all outdoor and indoor solar panel wiring applications. Commonly used for PV module wiring. Water and sunlight resistant. UL approved for use without conduit. Also known as type TC (tray cable). Complies with NEC article 340 and 690 and is rated as sunlight and moisture resistant, 90 degree C. Suitable for direct burial. Color may be White/Black, White/Red, or Black/Black.
We recommend #10 or #12 for wiring most solar electric panels with junction boxes, and #8 for higher amperage or long runs from the solar panel combiner or junction box to the charge controller or battery system. For utility tie (grid tie) where much higher voltages are involved at lower current, you can usually use #12 for all wiring from the solar panels to the inverter unless it is a very long run or you have a very large PV array.